By Gary Mintchell, Editorial Director Welcome to the fourth column in this series covering industrial networking and how these networks benefit maintenance, reliability and operations functions in a plant. I have previously covered HART Communication Protocol, Foundation Fieldbus and the FDT standard for displaying status and diagnostic information from the field. This month’s topic is […]
Trending is crucial. Condition monitoring of your electrical equipment provides the type of data that helps you anticipate and plan future maintenance activities.
By Ken Bannister, Contributing Editor Symptom: “We’ve begun using a variety of single-point lubricators for remote plant bearings on HVAC rooftop units, cranes, conveyor drives, etc. While our bearing failure rate has decreased drastically, we still experience failures. Is that normal for this type of automated lubricator?” Diagnosis: Automatic single-point lubrication (SPL) devices are relatively […]
According to automation and controls giant Honeywell Process Solutions, true sustainability can’t be realized without factoring total cost of ownership into the calculation.
New technologies in the power industry can introduce new, perhaps massive, maintenance costs. What to do?
By Ron Spataro As your workforce continues to turn over, are your new hires prepared to avoid the hazards of electricity? If there is an electrical accident in your facility, or you are in a high-risk industry, you’ve got pretty good chances of getting a visit from OSHA. In a one-year period, OSHA issued $26,460,902 in penalties […]
PLC Boiler Controls Clayton Compusteam PLC Control Systems are standard on all modulating models of the company’s boilers. They are available in three basic levels (I, II & III) with various options for expanding system capabilities. Compatible with Modbus, Ethernet/IP and Bacnet protocols, these PLC controls increase system reliability by making operating parameters readily available. […]
A renewable energy provider faced significant challenges on a geothermal project due to extreme degradation in critical piping. The heat and the highly corrosive nature of the geothermal liquids present at the steam source critically reduced the anticipated life of the originally specified carbon steel steam-supply system. Extensive research and testing prompted the plant managers to […]